AC Cooling and Air Conditioning Systems Berwyn, Illinois
At B&B Heating & Cooling, Inc., we install and service all brands of central air conditioning and cooling systems in Berwyn, IL. If you have an existing cooling system our trained staff can diagnosis your AC system and recommend terrific new high efficiency choices. We offer same day evaluation and prompt air conditioning installation services Berwyn, IL.
Let us help you decide how best to solve your air conditioning needs today.
Upon arrival the Tech. found the Lennox Furnace form 2014 not operating propperly due to a low flame signal. Cleaned the Furnace and flame Sensor. The unit was fully operational at depature.
Upon arrival the Tech. found the Frigidaire AC system not operating properly due to low refrigerant levels. Added 1lb. of R-22 Refrigerant. The Tech. also Chemically Cleaned the Condenser. The AC system was fully operational at departure.
Upon arrival the Tech. found the AC system working properly. The Tech. did find a dirty filter and told the resident they need to change their filter because the Tech. did not have one that size in his truck. The AC system was fully operational at departure.
Upon arrival the Tech. found there was an Air Flow issue on the second floor. The Tech. adjusted first floor registers to try to force air flow up to second floor. There are no dampers to adjust for the main supply run. There are temporary AC units on second floor but the tenant says they don’t keep up. *Recommend straight window AC units that would probably fix the problem. Second floor windows are sliders not double hung.*