Gas Furnaces Country club hills, Illinois
B&B Heating & Cooling, Inc. services all types of gas furnaces in Country club hills, IL. Our staff can diagnosis you existing systems and recommend terrific new high efficiency choices. We offer same day evaluation and prompt gas furnace installation services Country club hills, IL.
Let us help you decide how best to solve you gas heating problems.
While completing his Diagnostic, he found the Goodman Furnace had a "4-Flash" Error Code in its History, indicating the Furnace had an Open Limit. The Tech found the A-Coil was badly blocked, causing the Furnace to overheat and Trip the High Limit, due to this blockage. The A-Coil needs to be cleaned.
Country Club Hills, IL
Upon arrival the Tech. found the Ducane furnace was not operating properly due to a dirty flame sensor. Cleaned furnace and flame sensor. The unit was fully operational at departure.
Country Club HIlls, IL