Upon arrival the Tech. found the AC system not operating properly due to a dirty condenser coil and low refrigerant level. Chemically cleaned the condenser and added one pound of R410-A refrigerant. The AC system was fully operational at departure.
Upon arrival the Tech. found the Condensate Drain had been installed improperly, allowing the condensate water to leak onto the Furnace..
- A Condensate Pump will need to be installed to allow for property draining of the Condensate Water from the AC System.
(6/10/19) The Tech Installed the Condensate Pump and 3/8" Drain Tubing.
- During the installation, the A-Coil Drain Pan separated for the A-Coil due to the metal being rusted through.
* The AC System is an Amana R22 System from 1997. Based both upon age, as well as condition, replacement of the AC System is recommended.
Heil Heating & Cooling CA5536VKD
Upon arrival the Tech. found the Heil AC system not operating properly due to the unit being low on refrigerant . Added 1.5 lbs of R-22 Refrigerant. the AC unit was fuly operational at departure.