43 Total Reviews/files//bb-heating-cooling-logo.png708-403-2276$13010 W 159th St Ste 1, Homer Glen IL
AC Cooling And Air Conditioning Systems New Lenox, Illinois
At B&B Heating & Cooling, Inc., we install and service all brands of central air conditioning and cooling systems in New Lenox, IL. If you have an existing cooling system our trained staff can diagnosis your AC system and recommend terrific new high efficiency choices. We offer same day evaluation and prompt air conditioning installation services New Lenox, IL.
Let us help you decide how best to solve your air conditioning needs today.
Get Your Quote Today
B&B Heating & Cooling, Inc. AC Cooling And Air Conditioning Systems New Lenox, Illinois
Recent AC Cooling And Air Conditioning Systems New Lenox, Illinois by B&B Heating & Cooling, Inc.
ADPTG1K648D175B2205 Upon arrival the Tech. found the American Standard AC System from 2003 is not cooling due to being low on R22 Refrigerant. An Electronic Leak Check was performed, and a leak was found in the A-Coil. At a minimum, the A-Coil will need to be replaced and the AC System Pressure Tested, Pumped into a Vacuum, and Charged to Manufacturer Specifications. New Lenox,
GoodmanVSX130361 Upon arrival the Tech. found the Goodman AC system from 2016 running at very high head pressure. Chemcially Cleaned the Condenser that was completely blocked. Also had to remove some Freon, because the unit was way over charged. Pressures are better but still creeps higher then goes back down. Superheat number is correct with the Freon Charge. Found water leak to be a bad piercing valve on water line. New Lenox,
VSX130361 Upon Arrival The Tech. Found The I.C.P. R22 AC System From 1995 Was Not Working Due To An Un-repairable Leak At The Evaporator Coil. Our Recommendation Is To Replace The Existing AC System With A Goodman 2-1/2 Ton 13 SEER (R410A) Condenser, A Matched 2-1/2 Ton A-Coil, Fabricate And Install A Custom Sheet Metal Transition To Accommodate The New A-Coil, Flush The Existing Refrigerant Lines, Replace The Electrical Whip At The New AC Condenser, And Pressure Test, Pump Into Vacuum, And Check That The AC System Is At Manufacturers Refrigerant Specifications. New Lenox, IL 08-07-2019
American Standard HVAC7A0048A1000 Conducted Spring PM on one American Standard unit. Inspected refrigerant levels and electrical components and cleaned condenser. AC fully operational at departure. New Lenox,