Furnace Repair in Chicago, Illinois
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Chicago, IL is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call B&B Heating & Cooling, Inc. now. We fix broken heating equipment all the time in Chicago, IL. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
Upon arrival the Tech. found the Gas was shut off on the Trane Furnace from 2004.due to carbon monoxide detection. Found a breach where the Hot Water Heater and Furnace uses the chimney as a chase. After Chimney was cleaned - Reconnected gas pipe from gas Co. disconnect, and relight pilot on furnace and Hot Water Heater.
Upon arrival the Tech. Found the Trane furnace not operating properly due to a faulty pressure switch. Cleaned the furnace, replaced the pressure switch and cycled the unit. Furnace is now operating properly