45 Total Reviews/files//bb-heating-cooling-logo.png708-403-2276$13010 W 159th St Ste 1, Homer Glen IL
Air Conditioning Service, Repair And Installation Oak Forest, Illinois
B&B Heating & Cooling, Inc. is one of the leading providers of air conditioning repair and air conditioning service in Oak Forest, IL, offering timely solutions to problems related to your air conditioning system. Our HVAC technicians will come to your rescue when you want emergency AC service or repair, or just need a hand with your residential or commercial cooling problems.
You'll find we take our job seriously and highly value the trust that is placed in us. B&B Heating & Cooling, Inc. goes far beyond what others do by investing in the training and equipment necessary to protect your home or family in Oak Forest, IL.
Whether you have a central AC system, Heat Pump or Ductless Mini Split we are here to help.
Get Your Quote Today
B&B Heating & Cooling, Inc. Air Conditioning Service, Repair And Installation Oak Forest, Illinois
Recent Air Conditioning Service, Repair And Installation Oak Forest, Illinois by B&B Heating & Cooling, Inc.
GoodmanA42-15 Upon arrival the Tech. found the AC system not operating properly due to a blown 12.5 µF capacitor. Replaced the 12.5 µF capacitor and cycled the unit. The AC was fully operational at departure. Oak Forest,
Lennox13ACX-036 Upon arrival the Tech. found the Lennox R410A AC System from 2014 was not working due to having Low Refrigerant in the AC System. An Electronic Leak Test was performed, and leaks were found at both the A-Coil & Condenser.
* After checking with the Manufacturer we found both Condenser & A-Coil are beyond the 5-Year Warranty, therefore, we recommend replacement with a Lennox 3-Ton 13 SEER (R410A) Condenser, a matched 3-Ton A-Coil, and, Set the Condenser on the existing AC Pad, then Pressure Test, Pump into Vacuum, and Check that the AC System is at Manufacturers Refrigerant Specification. Oak Forest,
Carrier24ABB336 Upon arrival the Tech. found the Carrier AC system from 2014 not operating properly due to a faulty Capacitor. Replaced the 45+5 Capacitor and ran the system. The AC was fully operational at departure. Oak Forest,
CarrierCA13NA048 Complaint of Furnace making a noise
- Upon arrival the Tech. found the Carrier Furnace not operating properly due to a faulty capacitor. Replaced the Capacitor. The Furnace was fully operational at departure. Oak Forest,