45 Total Reviews/files//bb-heating-cooling-logo.png708-403-2276$13010 W 159th St Ste 1, Homer Glen IL
Air Conditioning Service, Repair And Installation Plainfield, Illinois
B&B Heating & Cooling, Inc. is one of the leading providers of air conditioning repair and air conditioning service in Plainfield, IL, offering timely solutions to problems related to your air conditioning system. Our HVAC technicians will come to your rescue when you want emergency AC service or repair, or just need a hand with your residential or commercial cooling problems.
You'll find we take our job seriously and highly value the trust that is placed in us. B&B Heating & Cooling, Inc. goes far beyond what others do by investing in the training and equipment necessary to protect your home or family in Plainfield, IL.
Whether you have a central AC system, Heat Pump or Ductless Mini Split we are here to help.
Get Your Quote Today
B&B Heating & Cooling, Inc. Air Conditioning Service, Repair And Installation Plainfield, Illinois
Recent Air Conditioning Service, Repair And Installation Plainfield, Illinois by B&B Heating & Cooling, Inc.
Lennox13ACX-036 Upon arrival the Tech. found the Lennox AC system not operating properly due to low refrigerant levels. The Tech. added 1lb. of R-410A. The AC was fully operational at departure. Plainfield,
GoodmanGMH80603A Upon arrival the Tech. found that there was a new filter that had been sucked into the the Blower Wheel . After removal of the Filter, the Furnace still has a slight vibration. The AC System is cooling properly, but the Blower Wheel needs to be replaced.
The Blower Wheel should be to replace on the Furnace. Please note that the Wheel is not covered under a Parts Warranty as the Goodman Warranty is only valid for the installing homeowner. If we don't know the correct name of that person, it will not be covered under the warranty. Plainfield,
American Standard HVAC7A0036A1000 Upon arrival the Tech. found the AC system not operating due to low refrigerant levels. Added 2lbs. of R-22 Refrigerant. The AC was fully operational at departure.
received phone approval for $302.56 from George Bellows @ IH per phone onsite NTE increase request from tech Steven @ Affiliate. Bruce Kniffin/SME-HVAC Plainfield,
GoodmanGSX130301ASplit Air Conditioner Upon arrival the Tech. found the Goodman AC system from 2013 not operating properly due to a faulty Contactor. The Tech. replaced the 40 Amp Contactor. The AC was fully operational at departure. Plainfield,
Trane2TTR3036A1000A Upon arrival the Tech. found the Trane AC system not operating due to a faulty Capacitor. The Tech. replaced the 45/5 capacitor and checked the system. The AC was fully operational at departure. Plainfield,
Lennox13ACX-048 Upon arrival the Tech. found the Carrier R22 AC System from 2001 was not working due to a bad Compressor. Although it appears the Capacitor was recently replaced, and a Hard Start Kit had been installed, the Compressor won't stay running and is making alot of noise.
* Based upon both Age as well as the System being an R22 System we recommend replacement with a Lennox 4-Ton 13 SEER (R410A) Condenser, a matched 4-Ton A-Coil, Fabricate and Install a Custom Sheet Metal Transition to accommodate the new A-Coil, Flush the existing refrigerant lines, Replace the Electrical Whip at the New AC Condenser, Set the Condenser on the existing AC Pad, and Pressure Test, Pump into Vacuum, and Check that the AC System is at Manufacturers Refrigerant Specification. Plainfield,
13ACX-048 Upon Arrival The Tech. Found The AC System Fully Operational. The Resident Had The Thermostat Set To 60 Degrees And It Was 70 Degrees In The House. The Tech. Informed The Resident That The System Can Only Do A 15-20 Degree Difference From What The Temperature Is Outside. The AC Was Fully Operational At Departure Plainfield, IL 08-16-2019
13ACX-048 Upon Arrival The Tech. Found The AC System Not Operating Properly Due To A Faulty Capacitor. Replaced The 35+5 Capacitor. The AC System Was Fully Operational At Departure. Plainfield, IL 08-16-2019