Furnace Service and Repair Bolingbrook, Illinois
If your heating system in Bolingbrook, IL is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Bolingbrook, IL. B&B Heating & Cooling, Inc. has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on B&B Heating & Cooling, Inc. to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
Found furnace inoperable due to a hole inside the heat exchanger. Replaced furnace and installed a Lennox 70,000 Upflow
Upon arrival theTech found the Furnace was fully operational. The dampers have been adjusted. Set the thermostat to "fan on" to get better air flow.
Upon arrival the Tech. found the Armstrong Furnace not working due to batteries not installed properly. Found the furnace had a low flame signal and needed to be cleaned. When fired up - the blower housing was loose - tighten the bolts on Blower housing. - The furnace was fully operational at departure.
Upon arrival the tech. found unit not calling "w" wire at IFC board was not secured behind terminal on board. Tighten wire connection, found unit had low flame signal. Cleaned furnace
Upon arrival the Tech. found the Rheem Furnace from 2003 had a bad Blower Motor. The Blower Motor & Capacitor will need replacement.