Furnace Repair in Aurora, Illinois
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Aurora, IL is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call B&B Heating & Cooling, Inc. now. We fix broken heating equipment all the time in Aurora, IL. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
Upon arrival the Tech. found the furnace not operating properly due to a faulty thermostat and dirty flame sensor. The Tech. replaced the thermostat and cleaned the furnace and flame sensor. The furnace was fully operational at departure
Upon arrival the Tech. found the Rheem furnace not operating due to a faulty high limit switch, broken igniter and dirty flame sensor. Cleaned the furnace and flame sensor, replaced the high limit switch and igniter. The furnace was fully operational at departure.
Upon arrival the Tech. found that the Carrier Furnace was tripping the limit, the Furnace would re-try, run again, and then trip the limit. The Limit was removed and the Heat Exchangers were inspected. Cracks were found in the Heat Exchangers, and therefore, at this time we would recommend replacement of the Furnace. We had recently replaced the Circuit Board in the Furnace, and we charged $221.00 for the Circuit Board. This price has been deducted from the price of the Furnace which would normally be $752.70 for the 90,000 Btu 80% AFUE with the ECM Motor as the non-ECM motor furnace is no longer available.
Please forward your approval.
Upon arrival the Tech. found the furnace not operating due to a dirty flame sensor. The Tech. cleaned the furnace and flame sensor. The furnace was fully operational at departure.