Furnace Service and Repair Plainfield, Illinois
If your gas furnace in Plainfield, IL is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Plainfield, IL. B&B Heating & Cooling, Inc. has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on B&B Heating & Cooling, Inc. to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace service in Plainfield, IL
We provide gas furnace repair in Plainfield, IL
Upon arrival the Techh. found the Bryant furnace from 2004 ws inoperable due to a faulty Ignitor and a low flame signal. Replace the Igniter and cleaned the furnace and flame sensor, the unit was fully operational at departure.
Upon arrival the Tech. found the Goodman furnace not igniting. Found a faulty HSI. The HSI needed to be replaced.Also there was a low flame signal - Cleaned the Furance and Flame Sensor.
Upon arrival the Tech found the Tappen Furnace operating but the circuit board was not wired properly. Corrected witing to circuit board ant furnace. Cl;eaned Furnace and Flame Sensor. AC was running at the same tome as furnace due to a bad 40 amp contactor on AC condenser - Repalced Contactor. The Unit was fully operational at departure.