No Heat in Plainfield, Illinois
Furnaces can be intimidating especially when they're not working. However there might be a silver lining to this stressful situation: roughly a quarter of all service calls can be resolved with easy fixes that are simple and inexpensive.
At B&B Heating & Cooling, Inc. we help homeowners like you in Plainfield, IL all the time with their heating systems. From simply offering advise, to complete system replacement, we have the knowledge and experience to help you resolve the challenges your heating system is presenting in the best possible way.
Upon arrival the Tech found the Tappen Furnace operating but the circuit board was not wired properly. Corrected witing to circuit board ant furnace. Cl;eaned Furnace and Flame Sensor. AC was running at the same tome as furnace due to a bad 40 amp contactor on AC condenser - Repalced Contactor. The Unit was fully operational at departure.
Upon arrival the Techh. found the Bryant furnace from 2004 ws inoperable due to a faulty Ignitor and a low flame signal. Replace the Igniter and cleaned the furnace and flame sensor, the unit was fully operational at departure.
Upon arrival the Tech. found the Goodman furnace not igniting. Found a faulty HSI. The HSI needed to be replaced.Also there was a low flame signal - Cleaned the Furance and Flame Sensor.