Gas Furnaces Bolingbrook, Illinois
B&B Heating & Cooling, Inc. services all types of gas furnaces in Bolingbrook, IL. Our staff can diagnosis you existing systems and recommend terrific new high efficiency choices. We offer same day evaluation and prompt gas furnace installation services Bolingbrook, IL.
Let us help you decide how best to solve you gas heating problems.
Upon arrivla the Tech. found the Lennox Furnance from 2008 not operating properly due to a low flame signal and debris in the Inducer Port. Cleaned the Furnace and Flame Sensor and Cleared debris from the Inducer Port. The Unit was fully operational at departure.
Upon arrival Tech. found the furnace not operating properly due to a dirty flame sensor. Cleaned the furnace
Upon arrival the Tech. found the Goodman furnace not working properly due to a dirty flame sensor. Cleaned the furnace and flame sensor. The unit was fully operational at departure.
Upon arrival the Tech. found the Goodman Furnace from 2003 that has a Flame Sensor that was giving .28 MicroAmp Flame Sense Reading at arrival, it only improved minimally after cleaning. The Flame Sensor needs replacement.
Upon arrival the tech found the Goodman Furnace was fully operational. Discovered the rain cap on rooftop was missing. Replaced the missing exhaust rain cap.
Upon arrival the Tech. found the Goodman Furnace from 2014 was operating properly. The Goodman Furnace from 2014 needs to be cleaned. Took Supply Temp at Master Bedroom, and instructed Resident on how to Program the Thermostat. The 6" Versa Cap needs replacement.\