Orland park, Illinois
Upon arrival the Tech. found the AC system not operating properly due to the Condenser being blocked. Chemically Cleaned the Condenser. Checked the Freon Levels and noticed the Freon Levels were low. Added 1lb. of R-410A Refrigerant. The AC system was fully operational at departure.
Orland Park, IL